£610.90 Excl. VAT
Product Code – 2CDG110199R0011
Product Datasheet – ABB DALI/KNX GATEWAY
Estimated Delivery – 1-2 Weeks.
You’ll receive a shipping confirmation once your order has been dispatched, confirming your delivery date and tracking.
Available on back-order
ABB DG/S188.8.131.52 DALI Gateway, Basic, 2-fold, MDRC
The ABB KNX DALI-Gateway DG/S 1.1 is a modular installation device with a module width of 4 units in proM design for installation in the distribution board. The connection to the KNX Bus is established using the bus connecting terminal at the front of the device. The assignment of the physical addresses as well as the parameterisation is carried out with the
The 1-fold DALI-Gateway (DALI = Digital Addressable Lighting Interface) is used for controlling DALI equipment (ballasts, transformers, LED converters, actuators, etc.) via EIB / KNX.
The DALI addresses are allocated individually and automatically by the DG/S 1.1. A change of the DALI addresses is possible if required with the separate DGS11 Software Tool, even without ETS. The 64 DALI devices connected to the main channel A can be directly switched, dimmed or controlled with a brightness value using just one EIB / KNX communication object. The scanning of the individual lamp or ballast fault, as well as the activation of a burn-in time or slave operation for every device, is implemented using coded address-based control with two communication objects. All 128 DALI devices connected to a second auxiliary channel B can be individually controlled using broadcast mode or address- based control. Primarily, auxiliary channel B is a broadcast channel which is used to control all devices from a common source.
Furthermore, the setting of 15 light scenes via the ETS or via the EIB / KNX communication object is possible via a push button. The light scene can be combined from any of the 128 DALI devices connected to the gateway. Both channels can be controlled or scanned independently of each other via broadcast commands.
The lamp burn-in time can be activated individually via coded control or commonly for all 128 devices.
Group assignment of the DALI devices is implemented with the EIB / KNX group functions.
The DALI-Gateway DG/S 1.1 requires an AC or DC auxiliary voltage. The DALI voltage required for DALI devices is generated by the gateway. 64 DALI devices per channel can be supplied with power.
|Dimensions||6.4 × 7 × 9 cm|